Mounting naturbo therm
The easiest way to install the naturbo therm wall heating boards is to watch our processing videos:
You can find further mounting videos under naturbo videos
Overview of the installation of naturbo therm wall heating boards
The processing of naturbo therm clay boards is explained in five simple steps. The ingenious plug-in module system makes it extremely easy to process the wall heating system flexibly, easily and quickly.
1st work step: Mounting the board
One starts with the installation of naturbo therm board and fills the remaining areas with naturbo clima panels. To avoid cross joints, naturbo therm boards are alternately processed in two different lengths (see Fig. 4).
The lower naturbo therm boards must be flush with the finished floor height. Use spacer blocks.
2nd work step: Fitting press couplings
The press couplings are fitted onto the upper heating pipes of the naturbo therm intermediate board.
3rd step: naturbo therm put on end board
The naturbo therm end board is lifted over the intermediate board and carefully brought into position. It is recommended to work in pairs: While one holds the boards, ...
... the other one inserts the heating pipes into the attached press couplings.
4th work step: Grouting
Now all connection points are pressed and checked for tightness by a heating specialist.
5. step: Close the press window
The press windows of the connection points are filled with the supplied drywall blocks and filled as usual (see naturbo clima).
The course of the heating pipes is marked on the surface of the naturbo therm board. The pipes run in such a way that the installation of sockets and switches is possible.
Up to 8 naturbo therm boards can be connected to a heating circuit.